ABHR Dispensers in Patient Rooms
by Bob Armbrister, on Nov 6, 2019 12:00:00 AM
Q: In the 2012 LSC concerning alcohol based hand rub (ABHR) dispensers in a hospital setting, is there a limit to the number of dispensers that can be in a patient sleeping room? We are wanting to have additional dispensers available in the room, such as 1 on the wall, one attached to the bed and one tabletop dispenser at the nurse workstation in the room. In the 2012 codes, would this number be allowed?
A: There is not a limit to the number of ABHR dispensers permitted in a patient room, but there is a limit to the quantity of ABHR product in dispensers per smoke compartment. You are limited to 10 gallons of ABHR product in dispensers per smoke compartment. If, for instance, each dispenser is 1 liter of product, then that means you can only have 37 dispensers per smoke compartment.
Now, the 2012 LSC does allow you to have one dispenser per room not contribute to the aggregate total of ABHR product in dispensers per smoke compartment, so if you have 12 patient rooms in the smoke compartment and one dispenser in each room, then that means you could increase the total ABHR dispensers from 37 to 49. And you must include in the aggregate total all pocket-sized dispensers and all table-top dispensers. This rule is not limited to just wall-mounted dispensers.