Our Life Safety educational resource hub is full of healthcare knowledge to help you be better informed of the changing world around you.
Rather than sit back and act on decisions made by others, we are leading the charge as it relates to identifying best practices for Life Safety Code® and compliance. We have real people that give our clients real information that can be put into practice.
Q: Are battery-operated task lighting required to be at Transfer Switch locations? We are getting some feedback that they are being required by NFPA 99-2012, section 126.96.36.199.3.2(4) and NFPA 70. These particular code references apply to generator sets but not ATS. Have you heard if CMS or any of the accreditation organizations are requiring these battery-operated emergency lights at ATS locations? Most of ours are located outside. I have also conferred with our electrical engineer and he has not heard or seen anything requiring this.
A: No, I have not heard that any national AHJ is requiring them at ATS locations. However, an AHJ can require it if they want to - that’s their prerogative.