Our Life Safety educational resource hub is full of healthcare knowledge to help you be better informed of the changing world around you.
Rather than sit back and act on decisions made by others, we are leading the charge as it relates to identifying best practices for Life Safety Code® and compliance. We have real people that give our clients real information that can be put into practice.
Q: Is there a standard on lighting of offices and exam room in the ambulatory or clinics?
A: The Life Safety Code is primarily concerned about egressing the facility under emergency conditions, and only has illumination requirements for emergency egress situations. Section 220.127.116.11 of the 2012 Life Safety Code says the floors and other walking surfaces within exits, and designated stairs, aisles, ramps, escalators, passageways, and exit discharges to be illuminated to 10 ft-candles for new conditions, and 1 ft-candle for existing conditions. Assembly occupancies are permitted to have 0.2 ft-candles of illumination. This applies to clinics and ambulatory healthcare occupancies. Please check with your state and local authorities to determine if they have more restrictive requirements.