Our Life Safety educational resource hub is full of healthcare knowledge to help you be better informed of the changing world around you.
Rather than sit back and act on decisions made by others, we are leading the charge as it relates to identifying best practices for Life Safety Code® and compliance. We have real people that give our clients real information that can be put into practice.
Q: Are there any regular testing requirements for Generator Remote Shutdown Switches?
A: Yes… sort of. Section 8.4.1 of NFPA 110-2010 says generators, including all appurtenant components, shall be inspected weekly and exercised under load at least monthly.
The term “appurtenant components” means accessory components, and the remote shutoff switch would be included in that. So, technically, you are required to inspect the remote shutoff switch weekly and exercise it when the generator is operating. You would not want to exercise this switch while the generator is under a load from the building, but rather during the 'cool-down' period after the test.
I have already seen a finding from a state agency that cited a facility for not testing the switch. It seems to be a ‘ticky-tack’ finding, but the surveyors are getting tougher because CMS is continuing to crack-down on Life Safety Code issues. But the bottom line… NFPA 110-2010 does require you to inspect it weekly and test it monthly.