Our Life Safety educational resource hub is full of healthcare knowledge to help you be better informed of the changing world around you.
Rather than sit back and act on decisions made by others, we are leading the charge as it relates to identifying best practices for Life Safety Code® and compliance. We have real people that give our clients real information that can be put into practice.
Q: We sometimes take patients into the stairwells for physical therapy. Does the NFPA codes restrict this activity? If we can continue to use the stairwell, can we have emergency pulls or some other type of emergency notification device in the stairwell when a therapist is in the stairwell with the patient?
A: You did not say what occupancy your facility is. Are you a hospital? A nursing home? A clinic? Or an ambulatory surgical center?
The quick answer is you cannot use an exit enclosure (i.e. stairwell) for any purpose that has the potential to interfere with its use as an exit (see section 220.127.116.11.3 of the 2012 LSC). A physical therapist assisting a patient with therapy in a stairwell would be considered an impediment to other people trying to egress if a fire emergency were to break out, and is definitely a problem and should not happen.
No, you cannot install emergency notification devices in the stairwell because section 18.104.22.168.1 (10) is very limited and says they are not permitted if they do not serve the stairwell.
You need to find a better place for PT activities involving stairs, and not in the corridor either.