Our Life Safety educational resource hub is full of healthcare knowledge to help you be better informed of the changing world around you.
Rather than sit back and act on decisions made by others, we are leading the charge as it relates to identifying best practices for Life Safety Code® and compliance. We have real people that give our clients real information that can be put into practice.
Q: In regards to the sensitivity testing of smoke detectors, I believe my fire alarm system is capable of complying with NFPA 72 for the sensitivity testing of smoke/heat initiating devices. For example: If we have a smoke detector that exceeds the expected sensitivity range it will send a trouble signal and the panel will show "dirty photo detector" and it will tell the device location. Additionally, we can run a complete report on all devices to show the current sensitivity value of each detector, this could be done on the alternating year frequency dictated by the code. I believe this meets NFPA 72-2010 requirements for sensitivity testing. Your thoughts, please.
A: I would agree with you. But when the surveyor asks for evidence that your smoke detector sensitivity was checked, what report do you show him? If you don’t print out a sensitivity report at least once every two years, you would have little to nothing to show them.