Our Life Safety educational resource hub is full of healthcare knowledge to help you be better informed of the changing world around you.
Rather than sit back and act on decisions made by others, we are leading the charge as it relates to identifying best practices for Life Safety Code® and compliance. We have real people that give our clients real information that can be put into practice.
Q: My question involves childproof outlets in healthcare. Where are they required and where in the code does it discuss not using snap-in covers?
A: According to NFPA 70-2011, Article 517.18(C), tamper-resistant receptacles are required in pediatric locations of health care facilities (i.e. hospitals, physician offices, therapy areas, etc.) including patient rooms, bathrooms, playrooms, activity rooms, and patient care areas of designated pediatric locations. As an option, the receptacle may use a listed tamper-resistant cover. The listing would have to be from an independent testing laboratory, such as UL, ETL, or the like. In essence, wherever an unattended child could be, you would have to have tamper-resistant receptacles.