Testing Elevator Fire-Fighters Service
by Brad Keyes, CHSP, on May 31, 2019 1:00:44 AM
Q: We have multiple hospitals that we provide fire-safety testing services to. With the new requirement for testing elevator fire-fighters emergency operations, we all have a different opinion about what needs to be done. I believe we need to test Phase I and Phase II. Some people believe its only Phase I and some believe its only Phase II that need to be tested. I even have one hospital that believes it’s only the emergency phone that needs to be tested. What is your opinion on this?
A: Well…. The hospital that believes only the phones need to be tested are not among the enlightened. They need to get a new understanding.
Section 184.108.40.206 of the 2012 Life Safety Code says all elevators equipped with firefighters’ emergency operations in accordance with section 9.4.3 (which references ASME A17.1 Safety Code for Elevators) shall be subject to a monthly operation with a written record. ASME A17.1 is the industry standard for Phase I and Phase II operations. Phase I is typically the recall portion, and Phase II is the in-cab operation of the fire fighters’ service. So, I would say both Phase I and Phase II must be operated monthly. Now, if the elevators are only equipped with Phase I, then of course you can’t test Phase II operations.